Consumer unit upgrade in Wilmslow, Cheshire
This was a great example of a very common type of work that we undertake and there is many properties that are in need of fuse box upgrade to increase safety and to establish current condition of the electrical installation.
Project was started by thorough inspection of the existing electrical installation and this revealed several potentialy dangerous problems.
- immersion heater incorrectly connected on the electrode causing potential fire risk
- absence of circuit protective conductor (CPC) to outdoor security lights causing potential danger of electric shock from class 1 equipment
- lack of RCD protection
After the inspection and testing was complete and the faults that required immediate attention rectified, we procede to replace the consumer unit and than tested final circuits again to ensure correct connection of all conductors.
This is what the client has to say about the work we carried out.